A critical data center with six (6) large 80 HP cooling towers each having energy efficient motors, new bearings, pulleys, and shafts installed by Comfort International Inc. whom made these critical repairs without disrupting the 24/7 data center operations.
Due to the confined space and piping arrangement we had to remove and rig sections of the very large diameter piping to enable the new parts to be installed. Some of the bearings had insufficient clearances to use a puller so we had to cut the old bearings out to replace them with new bearings. The chief engineer was pleasantly surprised that this critical labor intensive project that other contractors would have taken six weeks to accomplish was done by Comfort International Inc. in a mere 2 weeks. We at Comfort International Inc. can handle any of your critical data center or large central plant service and repair needs.